Waste type: healthcare waste
Waste density: 125 to 350Kg/M3
Waste calorific worth: 4000KCAL/kg
Moisture web content: 10– 25%.
Estimated ash deposit: 5– 10%.
Nominal ability: 50kg/hr set load.
Second chamber: 2 [e-mail shielded] C.
Environmental: NEMA ACT (EMCA) 1999, Waste Monitoring policies, 2006.
Key Burning chamber:.
The main burning chamber is the major framework of the burner, produced from mild steel plate as well as tensed with rolled steel sections.
It is lugged from the flooring degree on a substantial steel support structure. Inside the covering is lined with calcium silicate insulation and also a warm face combination of extremely obligation brickwork or high stamina castable.
The primary burning chamber must make sure minimum departure temperature is not much less than 850? C.
One Hand-operated Lots Burner making up:.
Hand-operated filling door.
Straight solid fireplace, refractory lined primary burning chamber. Approx. measurements 800x2100mm( DxL).
Complete sized bulk load/ash elimination door.
1 off diesel-fired ignition burner– temperature managed.
1 off combustion air supply fan as well as distribution system, automatic control.
High capability secondary burning chamber with house time not much less than 2 seconds @>> 850? C.
1 off diesel-fired afterburner– temperature controlled.
Control panel– automatic procedure.
Temperature indication primary and additional chambers 0-1200? C.
Refractory lined flanged chimney to an elevation of 10M above ground degree.
NB: The additional combustion chamber must ensure that the gas temperature as gauged against the inside wall in the second chamber & & not in the flame area, is not less than 1100? C
Throughput: 50kg/hr at a small calorific value of 4,000 kca/kg as well as a typical mass thickness of 120kg/m3 for basic waste as well as 160kg/m3 for health care waste.
Ash: The waste will be decreased by 90 ~ 95% to leave 10-5% ash.
Quality/Environmental Criteria: NEMA ACT (EMCA) 1999, BS3316.
Operating duration: anticipated daily operating period 8 hours.
Maximum operating duration: 12 hrs.
Chamber: should be refractory lined to the list below requirement;.
Hearth and also reduced section of chamber wall surfaces.
Hot face product:.
Super obligation firebrick.
Restricting constant service restriction 1500? C.
Thermal conductivity: 1.3 W/mk.
Limiting continuous service limit 1000? C.
Thermal conductivity: 0.095 W/mk.
Chimney/Stack: Ought to be made from refractory lined moderate steel or excellent quality air-cooled s/s.
The chimney/stack should have a minimum height of 10m over ground degree.
Ignition heaters: fully packaged oil kind, total with electrical ignition as well as fire failure controls, wired with continuous running follower as well as full with all shutoffs, follower as well as motor.
Maximum rating: at least 450kW/hr.
Burner: scheduled on/off operation.
Maximum consumption: at least 6Ltrs/hr.
Average intake: a minimum of 3Ltrs/hr.
fully packaged oil kind, total with electric ignition and also fire failing controls, wired with continual running follower and also total with all valves, fan and also motor.
Optimum score: at least 450kW/hr.
Heater: arranged for on/off procedure.
Optimum usage: at the very least 9Ltrs/hr.
Typical usage: at least 4.5 Ltrs/hr.
Flue gas therapy: should have particulate eliminator (scrubbers).
Electric supply: solitary phase: 220/240VAC; 50/60Hz
clinical waste burner to buy Procedure guidebook: 2 collections.
Service/maintenance handbook: 2 sets.
Certification: NEMA (or other recognized) qualification.
Capacity to service equipment: the agent/supplier will have sufficient facilities, spare parts, consumables and also qualified competent technological team.
Training: the Agent will carry out a two days burners training after installation and also appointing of the tools.
The Representative will perform a 2 days operation & & maintenance training to the Biomedical engineering employees after installation & & appointing of the equipment.